Comparison of brightness of illuminator
Is it really so though the inverter illuminator is advertised, "It is bright and conservation of energy", "The flicker is few", "Light soon", and "The noise is low"?I was doubted for years. Because the wattmeter and the luminometer had been obtained this time, the comparison measurement was done as the thing of a usual stabilizer (Gros type).
Brightness comparison and result of a measurement of illuminator
As for the inverter illuminator, if it is the same power consumption compared with the illuminator of a usual stabilizer (Gros type), it is understood that it is about 20% bright as a result. However, when the apparatus of the inverter is used because of a dark setting, it can be said that neither the thing nor the efficiency of a usual stabilizer will change.
Brightness comparison and measuring method of illuminator
The inverter illuminator is HD8823T-R76 of the Japanese style hanging type of National, and 32W+30W. The illuminator of a usual stabilizer for the comparison (Gros type) is HD925 of the Japanese style hanging type of National, and 32W+30W.
- To lose the influence of [se-do], [se-do] is removed. Externals of apparatus are almost the same sizes.
- Brightness was measured in a place away downward from a fluorescent tube by 50cm. The indoor brightness was about 20Lux.
- A fluorescent tube had done aging for about five minutes before it measured it respectively by using the same thing with FCL32EXN30 and FCL30EXN28 of National.
- Wattmeter---M-3860M of METEX
- Luminometer---MS8209 digital multimeter of MASTECH
I see ..about 20% bright.. if it is illuminator of a usual stabilizer (Gros type) power consumption as written in the catalog that is the more same compared with. the inverter illuminatorI see at it is time when this however is the most efficient when doing to the setting with dark brightness ..little change...
If it is a difference of such brightness, it is actually extent that doesn't understand even if it compares it. There are a lot of breakdowns, and the repair charge costs much in the illuminator of the inverter, too. I think that I cannot say that it is a too good product even if the price of the product is also high, and other advantages are considered. I do not think that I finally become conservation of energy and a saving resource if the longevity of the illuminator is short though it is said that it is conservation of energy.